Greenstar 24i boiler manual sWorcester Boiler ManualsOur Services & Information
Worcester Bosch Boiler Manuals Shown below are boiler manuals. Click on the manual to open it. Alternatively right click to save to a custom location. The manuals title will indicate if they are installation,user manual or other types of manuals or resources. In due course we will provided the ability to search on multiple terms and by GC no. Need a manual for your Worcester Greenstar 24i System Gas Boiler? Below you can view and download the PDF manual for free. There are also frequently asked questions, a product rating and feedback from users to enable you to optimally use your product. View and Download Worcester GREENSTAR 24i junior instruction manual online. wall hung RSF gas-fired condensing combination boiler installation, commissioning & service. GREENSTAR 24i junior Boiler pdf manual download. Also for: Greenstar 28i junior, Greenstar 24i junior. Worcester GREENSTAR 24i junior Instruction Manual. Download Instruction manual of Worcester GREENSTAR 24i junior Boiler, Thermostat for Free or View it Online on luhost.xyz View and Download Worcester 24i junior user instructions & customer care manual online. 24i junior Boiler pdf manual download. Also for: 28i junior, 24 series, 28siii series.Quick Links. Table of Contents. Supplied By www. Related Manuals for Worcester 24i Boiler Worcester Greenstar 12i Instruction Manual Wall hung rsf gas fired condensing boiler, for sealed central heating systems and indirect fed domestic hot water 72 pages. Wall hung rsf gas fired condensing combination boiler for sealed central heating systems and mains fed domestic hot water 65 pages. Wall hung rsf gas fired condensing combination boiler, for sealed central heating systems and mains fed domestic hot water 64 pages. Wall hung rsf gas fired condensing system boiler for sealed central heating systems and indirectly fed domestic hot water 56 pages. How to Set Your Mechanical Boiler System Quick Links. Wall hung rsf gas fired condensing maunal boiler for sealed central heating systems and mains fed domestic hot water 65 pages. Wall hung rsf greenstar 24i boiler manual s fired condensing system boiler for sealed central heating systems and indirectly fed domestic hot water 56 pages. Wall mounted combination boilers for central heating and mains fed domestic hot water 44 pages. Wall hung gas-fired condensing combination boiler 21 pages.
Failure to install appliances correctly could lead to prosecution. Failure to comply with the guidelines for t he use of wat er treatment with the appliance will invalidate the appliance warranty.
NOTE: this is reduced to IP20 if the following mechanical timers are fitted: 7 or 7 See IEE wiring regulations. Electrical switches, fused spur and socket out let s must not be sit uat ed in t he bathroom.
This is fitted to the boiler frame. Minimum dimensions of flue terminal positions for balanced room sealed flues with fanned draught: DRWG. Protective clothing, footwear, gloves and safety goggles must be worn as appropriate. Remove outer carton A and place safely away from the working area. With the outer packaging removed and the inner sleeve B still in place gently lay the boiler on its back.
The boiler will lie at an angle to the floor to allow the boiler outer casing E to be removed. Do not lift by the air gas manifold. System pipes may be run vertically upwards behind the boiler or below it. See Plumbing Manifold Section on page Lower the control panel into the service position by removing the screw F from the retaining bracket.
Make connections to the heating system. Connect the gas supply to the boiler gas cock 22mm compression. NOTE: to ease the assembly of flue components, apply silicone lubricant to sealing surfaces. Subtract the length of the Standard Flue and turret mm from length L. Subtract the full length 1m extension s from the figure. Cut one of the 1m extensions to the remainder. Cut both tubes square taking care not to distort the tubes. Remove any burrs. The slope of the terminal outlet must face downwards.
Note: any external condensate pipework should be protected with weather resistant insulation to help prevent freezing. It must fall at least 50mm per metre towards the outlet. The isolator must have a contact separation of 3mm minimum in all poles.
External fuse rating 3A. When stripping wires always ensure copper strands do not fall into the control box. Open all radiator valves. Fill the system via a WRAS approved filling loop to 1 bar then turn the valve anti-clockwise to close. Vent A any air from the boiler heat exchanger using a suitable container to collect any water. Ensure tube outlet B is directed away from the fan or any other electrical component to prevent any water damage.
This is to allow sufficient time for this part of the commissioning procedure. It will be necessary to run water through the domestic hot water circuit to ensure that the boiler will not cycle on low heating demands. Replace top two screws A. Retighten bottom two screws B. Hold the panel up against the underside of the boiler and slide towards the rear until it is fully engaged.
Removing outer case A 1. Adjusting boiler control to service position 2. This is to allow sufficient time for the setting procedure. It will be necessary to run water through the DHW circuit to ensure that the boiler will not cycle on low heating demands. Undo and remove securing nut E from the top of the heat exchanger. Remove stainless steel viewing mirror F.
Lift up assembly and remove from boiler. Disconnect spark electrode and flame sensor connections J. Remove clamping plate K. Remove top baffle M. Remove baffle N. Remove the two hexagon headed screws O retaining the access cover P on the sump. Access the heat exchanger flue ways by inserting the cleaning brush 7 through the top access hole in the casing Q.
Clean heat exchanger flue ways R using the cleaning brush 7 removing any debris from the access point in the sump.
Removing outer case 1. To remove bottom tray, pull forward on the tag on the underside of the tray. Moving boiler control to service position 5. Gas valve 6. Access to boiler control components Remove 3 screws A and remove cover from control. There is a spare fuse clipped into the underside of the electrical cover. Remove 5 screws C retaining the rear panel of the control and remove panel.
Replacing control B The complete unit must be replaced. These can be unclipped from the plastic moulding noting their position. Remove the code plug B. The code plug should be left attached to the frame of the boiler by its plastic safety thread. Fan Re-assemble with new fan ensuring seals are correctly fitted. Electrode assembly Remove clamping plate D. Diverter valve motor Insure the appliance is in service mode there is no need to drain the appliance.
Disconnect the electrical connector from the diverter valve motor. The assembly will slide free from the valve. To refit, follow the above in reverse. Diverter valve Pump head Ensure the boiler is fully drained see draining the appliance.
Disconnect the electrical connection from the bottom of the pump. A Pressure gauge Hydraulic Block Disconnect the electrical connections to the NTC, Turbine and pump. Undo the nuts securing the copper water pipes to the manifold there is no need to remove the gas pipe Release the spring clips securing these water pipes to the plastic housing and remove the pipes.
Release the spring clip securing the expansion vessel pipe to the plastic housing and remove the pipe. Plastic protection device Disconnect all pipes connected to the pump housing. Remove the electrical connection to the pump. Withdraw the metal clip to the right of the pump head to release the pump housing. Slide the device to the left and then withdraw it from the appliance. Bypass valve Undo the screw securing the left hand plastic housing to the heat exchanger Move the housing to the left to free up the one end of the pipe.
Remove the pipe from the right hand housing to reveal the bypass valve CO2 should be measured after 10 minutes A B Worcester cannot be held responsible for costs incurred by persons not deemed to be competent. The electronic control system for this boiler incorporates a blue central indicator. This normally confirms the permanent mains supply but, by flashing at different rates during a fault, provides a guide to the cause as listed.
This fault finding system assumes that the appliance has been operating normally until the time of failure i. NO Spark ignition 4 seconds Stop spark.
Service Provider. Page 17 Minimum dimensions of flue terminal positions for balanced room sealed flues with fanned draught: DRWG. Page 22 Do not lift by the air gas manifold. Page 37 1. Page 43 5.
Related Manuals for Worcester GREENSTAR 24i Junior. Boiler Worcester GREENSTAR 24i junior Instruction Manual. Wall hung rsf gas fired condensing. Page 1 THE APPLIANCE IS FOR USE WITH NATURAL GAS OR L.P.G. (Cat II 2H3P TYPE C13 & C33) NATURAL GAS: WORCESTER GREENSTAR 24i junior . Worcester Greenstar 24i System ErP Pdf User Manuals. View online or download Wall hung RSF gas fired condensing system boiler. Brand: Worcester. Worcester GREENSTAR 24i Junior Installation Instructions Manual 76 pages The WORCESTER 24i or 28i is a combined domestic hot water and central. CONTENTS. CONTENTS. INSTALLATION & SERVICING INSTRUCTIONS FOR WORCESTER GREENSTAR 12i/24i System. 8 b (03/). 3. S. A.
this Greenstar 24i boiler manual s
CONTENTS. CONTENTS. INSTALLATION & SERVICING INSTRUCTIONS FOR WORCESTER GREENSTAR 24 i junior/28 i junior. 8 b (03/). S. Boiler Manuals for the Worcester 24I appliance. Worcester Boiler Manuals. Listed below are all the manuals for Worcester. junior · Worcester Greenstar 24i junior LPG · Worcester Greenstar 28i junior LPG. WORCESTER GREENSTAR 24i System GC NUMBER GB/IE. INSTRUCTION MANUAL. INSTALLATION,COMMISSIONING. & SERVICING. THESE INSTRUCTIONS ARE. APPLICABLE TO THE WORCESTER,. BOSCH GROUP BOILER MODEL(S). STATED ON THE FRONT COVER OF THIS. MANUAL. in the know. Swale Heating have an archive of Worcester Boiler Manuals, downloadable and free. Worcester Bosch 24i RSF GC No · Worcester. The WORCESTER 24i or 28i is a combined domestic hot water and central heating appliance. It consists of a gas fired boiler having a varying output of between. Here is a list of Worcester boiler manuals. We have spent many hours sourcing these manuals and adding the gas Worcester 24i Junior LPG Download a range of Worcester boiler manuals from Direct Heating Spares includes Worcester Greenstar, Worcester Worcester Greenstar 24I Junior LPG.greenstar 24i junior / 28i junior wall hung gas-fired condensing combination boiler for sealed central heating systems & domestic hot water user instructions & customer care guide this boiler is used with natural gas or lpg (cat ii 2h3p type c13, c33 & c53) natural gas 24i junior gc number: 47 86 28i junior gc number: 47 View and Download Worcester GREENSTAR 24i junior instruction manual online. wall hung RSF gas-fired condensing combination boiler installation, commissioning & service. GREENSTAR 24i junior boiler pdf manual download. Also for: Greenstar 28i junior. WORCESTER BOSCH GREENSTAR 12i & 24i SYSTEM OPERATING THE BOILER 8 a (06/) 7 SWITCHING THE BOILER ON/OFF Switching on Switch on the boiler by pressing the main power button. The indicator light shows blue Switching off Switch off the boiler by pressing the master switch. The blue indicator light goes out. SETTING THE TEMPERATURE. Page 1 INSTALLATION, COMMISSIONING AND SERVICING INSTRUCTIONS WALL HUNG RSF GAS FIRED CONDENSING COMBINATION BOILER GREENSTAR 24i Junior/28i Junior FOR SEALED CENTRAL HEATING SYSTEMS AND MAINS FED DOMESTIC HOT WATER The appliance is for use with Natural Gas or L.P.G. (Cat II 2H3P type C13, C33 & C53) ; Page 2: Table Of Contents. Worcester Greenstar 24i System Gas Boiler. Need a manual for your Worcester Greenstar 24i System Gas Boiler? Below you can view and download the PDF manual for free. There are also frequently asked questions, a product rating and feedback from users to enable you to optimally use your product. If this is not the manual you want, please contact us. View and Download Worcester GREENSTAR 24i junior instruction manual online. WALL HUNG RSF GAS FIRED CONDENSING COMBINATION BOILER, FOR SEALED CENTRAL HEATING SYSTEMS AND MAINS FED DOMESTIC HOT WATER. GREENSTAR 24i junior boiler pdf manual download. Also for: Greenstar 28i junior. The WORCESTER 24i or 28i is a combined domestic hot water and central heating appliance. It consists of a gas fired boiler having a varying output of between kW and kW (24i) or kw and kw (28i), a combined heat-exchanger and all necessary controls to provide mains fed . Greenstar i System Mk1 Installation and Servicing Instructions to Download (mb).